The panel is a GE TLM1612C, ns think.
You are watching: Will eaton breakers fit in a ge panel
TLDR: They"re all wrong. Swap through a GE or share breaker (e.g. Eaton CL no BR).
You can use numerous breakers within a panel.Breaker species which are provided on the panel"s labeling, these will certainly be made by the very same manufacturer and also the same type, and UL-listed. Breaker varieties which are modern-day to your panel"s labeling, yet again room still the exact same manufacturer, and also they state lock will work-related in your panel, or substitute for breakers which are labeled for use in her panel. Additionally UL-listed. Breakers which space made by a 3rd party, who sends them come Underwriter"s Laboratories to have actually them UL-listed for the competitor panel. UL phone call this a "UL-Classified" breaker, and also they operation the same collection of tests they operation on factory breakers. If you study the manufacturer the the breaker and their classified breaker lines, lock should show a cross-reference chart stating which manufacturing facility breakers their Classified breakers deserve to substitute for.
Classified is UL"s method of speak these are not OEM breakers and do not have actually the advantage of the OE"s expertise and trade-secret knowledge, yet they perform pass security testing.
Keep in mind the a manufacturer"s Classified breakers are different breakers 보다 the OEM breakers they do for their own panels. For instance, Siemens QD breakers space classified because that Square D QO panels, and have to not be offered in any kind of Siemens dashboard of any type of kind.
Similarly, girlfriend will watch that Eaton"s CL line of breakers is not UL-classified for usage in Eaton BR panels -- even though the breakers might look outwardly the same.
This have to not be perplexed with cross-listing. For instance, Challenger panels have actually breakers well-known to it is in defective (but panels are fine). Human being seeking to change those breakers uncover their dashboard labeling requires form C breakers. They space pleased to uncover that Eaton"s BR line is cross-listed as type BR and kind C.
On her panel, we can strike out the Square D breakers immediately. Square D is absolutely protest to "Classified" breakers. Castle refuse to make classified breakers for contender panels, and also they thing to the usage of divide breakers in your panels (not the they have actually anything come say about it). Therefore the Square D "HOMeline" breakers are out-of-place because Square D says so: You room using this breaker in contradiction come its labeling and also instructions, which violates NEC 110.3(B).
It likewise violates NEC 110.2, which requires all equipment must be approved.
Siemens does make classified breakers. They do the QD form for Square D "QO" panels, and the MSQ type also because that Square D "QO" panels. Now, Siemens" website just burned down for this reason Google is useless (every page is 404). But from Google"s see of your pages, it"s clean they don"t make UL-classified breakers for GE panels. Also if castle did, your MP-T type is no that; being made solely for Murray family tree panels. Together such, 110.3(B) and 110.2 apply, same as above.
The appropriate GE breakers room perfectly sensibly priced.
See more: Original Disc But No Cd Drive In Laptop: Star Wars Empire At War No Cd Patch
If they weren"t (QO isn"t), climate you could consider classified breakers made for that panel, such together Eaton CL. Do not usage Eaton BR; as pointed out earlier, a manufacturer"s classified lines are incompatible through their own panels, unless they are also classified because that their own panels (The fact Eaton didn"t divide the CL line for BR probably way they can"t.)