One worry that is generally faced through HVAC systems is high suction pressure.But what reasons high suction pressure? You need to have actually a an excellent understanding of her refrigeration bike to see what is happening in every process. If you execute not have an understanding then you will spend much more time guessing what the problem is rather of fixing the problem.
You are watching: High suction pressure low discharge pressure
The refrigeration cycle have to be examined. A an easy understanding of your refrigeration system is learning about the two operating systems. The two systems space suction pressure and also discharging pressure. There space both high and low settings for each press line.
For a high-pressure suction to happen you could have an insufficient compressor. An interpretation your refrigeration has actually a leaking discharge valve. This shows that your compressor cannot administer the required refrigerant come the evaporator to manage the cooling load. Without a required refrigerant, the produces a greater temperature and also pressure in ~ the outlet the the evaporator, which causes a high suction pressure.
Suction and also Discharging Pressure troubles Explained
High suction push is a trouble that can be easily determined and fixed. One means to identify if the difficulty is fixable is by analyzing your compressor. If her compressor piping and also amperage show up fine, then you should perform an additional analysis.
You deserve to perform an analysis by check the outlet the the evaporator, which is leave the refrigerant in ~ a high temperature. Your remote bulb should react and also move the electrical expansion valve, or EXC, come the opened direction to allow an ext refrigerant to circulation in the evaporator to take care of the cooling load.
If her temperature and pressure outlet that the evaporator or suction press keeps going increase it method you are having a trouble with her EXV.
Some factors you are having actually high suction pressure include:System load too highExpansion valve capacity as well highCapacity regulator as well largeHot gas bypass/capacity regulator defectiveSet also highOne or much more compressor disc valves leaking
What reasons Your Suction push to Rise?
When your compressor has both a short head pressure and also a high suction pressure your refrigeration equipment is quiet running, yet the temperature is dangerously low. Your compressor is still cooling, yet not cooling come its rated capacity.
Your medium temperature commodities will spoil quicker. The main reasons her compressor will have simultaneously short head pressure and also high suction push is early out to:Worn compressor piston ringsLeaky oil separator return line
Your compressor valves may end up being inefficient early to bad sealing from dirt and also debris deposits. Girlfriend may have actually experienced the slugging that refrigerant oil, moisture, and heat build-up or flooding problems. There may have been compressor overheating due to the fact that of undercharging your refrigerant or superheating your refrigerant. All space perfectly explainable reasons for having compressor problems.
Compressor overheating is a serious and most frequent difficulty for refrigerants. That’s why it’s essential to adjust the press reducing valves to protect against overheating the compressors.
Symptoms of a Leaky Valve
You should very closely monitor and examine even if it is or not you havehigher than typical discharge temperatureslow condensing head pressures and temperaturesnormal come high condenser subcoolingnormal to high superheatslow amp draw
If you notice higher than normal discharge temperatures, this shows your discharge valve is no sealing properly and also has been damaged. This directly reasons low head pressure. This causes the heating of the discharge gases to be recurring over and also over again. This causes higher than normal discharge temperatures.
You may likewise be suffering low head push from her valve. This is since some of the discharge gases space being short cycled native the compressor cylinder. This create a short refrigerant circulation to the condenser. This to produce a decreased heat load on the condenser that lowers the head pressures and temperatures.
If you room experiencing a greater subcooling, this is because there is a diminished refrigerant circulation through the condenser. Meaning, your whole system is flow at a lessened rate with the condenser. Most of your refrigerant is in your condenser and receiver.
You may likewise have high suction pressure. This procedure occurs due to the fact that the upstroke suction follow me the compressor’s cylinder sneaks earlier into the suction line. After all, the suction valve is no seating properly. The outcomes are higher suction pressure due to the fact that the refrigerant vapor throughout the downstroke is appropriately functioning, however the upstroke is mistakenly functioning.
You may also have a higher suction pressure because of a leaky discharge valve. This permits the discharge gas come sneak up right into the compressor’s cylinder throughout the downstroke. Her suction press increases because the suction valve is being open during the part of the downstroke of the compressor. This creates the cycle of high suction pressure, which loss your refrigerant.
What is a Worn Compressor Ring?
Worn compressor rings take place when the discharge gases leak with the compressor’s piston rings. This to produce a lower head pressure during the compression stroke in the system. The suction pressure is elevated due to the fact that the discharge gases have leaked with the rings. The an outcome is higher than normal suction pressure.
The results of having actually worn compressor rings create lower head press with high suction pressure. The results of having worn rings within her compressor appear comparable to having leaky valves.
Leaky Oil Separator Explained
Your oil separator controls her high and low political parties of her refrigeration system. This permits the oil to take trip from the oil separator to the compressor’s crankcase. Your oil separator is ~ above the high side of the system, if the compressor crankcase is ~ above the low side.
High press occurs as soon as the needle valve gets partially stuck open and also goes straight into the compressor’s crankcase. This reasons both high low-side pressures and low high-side pressures.
You should closely monitor even if it is or no the oil return line is over or listed below the ambient bordering temperature. If the heat is warm then the discharge gas is most most likely sneaking to the partially open needle valve in the oil separator.
Problems with Your electrical Expansion Valve
Electric growth valves permit for aid to keep and permit efficient regulate of the chiller during low fill or head pressure conditions. The EXV can manage the circulation of refrigerant that enters the direct expansion evaporator. They perform this in an answer to signals sent out to them by an digital controller. A tiny motor is provided to open and close the valve port.
If your suction pressure keeps rising within her refrigerator mechanism you need to examine on assorted parts of your refrigerator the include:The setups for superheatReplace your electrical expansion valveFind correct size
When friend are having trouble with your suction push you should examine to watch if the settings for superheating are correct. If this is still not correcting the difficulty you should examine your EXV to check out if the is functioning properly. It might need replacing. Girlfriend will require to uncover the ideal size because that the ideal refrigerant.
Condenser troubles Explained:
If her valve and compressor are all working effectively there room other possible reasons the suction press is high. One factor is her condenser might be dirty. There will certainly be a higher temperature if the lot of warm cannot it is in easily determined when utilizing the cooling medium. This create a higher temperature 보다 the style temperature in ~ the inlet the the evaporator.
The greater temperature at the inlet will result in high outlet temperature and also pressure and high suction push occurs. An additional possibility is having actually dryer problems. A dryer is a hold vessel that receives the liquid refrigerant native the outlet of the condenser.
The condenser’s primary function is to make sure only liquid refrigerant get the expansion valve. It additionally contains a substance the absorbs moisture to assist dry the end your refrigerator. If the dryer is clogged and also full of moisture, then much less liquid passes through it.
This creates less liquid come reach her evaporator, creating a higher temperature, and pressure in ~ the outlet will be high. This entire process creates a high suction pressure. Girlfriend should carefully examine what type of cool kind your condenser is. The species includeAir CooledWater Cooled
If the condenser is air-cooled type, climate the fan have to be sufficient sufficient to eliminate the warmth from the refrigerant. The temperature have to then revert to its basic setting. If your condenser is water-cooled climate the cooling water temperature and flow rate should have the ability to remove the warmth from the refrigerator. Her condenser is then in a subcooled state at the main set temperature.
Other reasons for High Suction Pressure
After carefully evaluating and considering every one of the previously mentioned possibilities for high suction pressure there are still various other reasons for having high suction pressure. In all of the previously discussed reasons, you probably assumed a high superheat, higher temperatures lead to higher pressure at the suction line.
Another element to consider is the overcharging the the refrigerant. Overcharging leads to overfeeding the evaporator through refrigerant, which leader to higher suction pressure.
See more: Does Rubber Is A Good Conductor Of Electricity ? Does Rubber Conduct Electricity
Another opportunity is having actually oversized EXV causes an overfeed to the evaporate, which boosts your suction pressure. Not every one of the reasons for high suction pressure is since of high superheat and greater temperatures.